Load bank testing is an essential part of good maintenance practices. Performing yearly load bank testing helps to extend the generator’s engine life.
WHAT IS LOAD BANK TESTING?
Load bank testing allows a standby generator to be tested and exercised to verify its overall reliability, and its ability to run at its full rated kw output. Typically, a generator is running at a level far less than the units rated output capability. Load banking checks the engines ability to perform and provide the required horsepower when called upon in an emergency. When a load bank is used, the artificial load it provides brings the engine up to an acceptable operating temperature.
WHAT IS NO-LOAD TESTING?
Most data center customers exercise their standby generators weekly un-loaded, but very rarely test them with building loads, relying on the occasional utility loss to do the testing. For diesel engine driven generator sets this can cause wet stacking. Wet stacking is when unburned fuel accumulates in the engine exhaust. This is caused by under loading a generator. When exercising a generator, or running it for short duration outages while under load, the engine may not reach its optimum operating temperature. When this is allowed to continue for long periods of time, the unburned fuel accumulates, and can become harmful to the engines efficiency and life span.
WHAT ARE THE BENEFITS OF LOAD BANK TESTING?
Load bank testing allows the engine to reach the full operating temperature and “burns out” this accumulation of un-burnt fuel. The result is a unit that runs cleaner and more efficiently. It also offers peace of mind that your standby generator is operating as it was designed to. Any generator set, whether the prime move is diesel or gaseous fuel driven, can benefit from having it load bank tested.
ALTERNATIVE ENERGY SOLUTIONS, LTD. LOAD BANK TESTING SERVICE
During the load bank test, we monitor critical engine parameters such as: oil pressure, engine temperature, fuel pressure, etc. We record these readings to show that once the unit reaches full rated load, it runs at normal operating temperatures and pressures. With this service, we provide a full report of the readings including generator output readings such as: voltages, amperages, kw amounts, etc.
Our company offers load bank testing as a separate service, or we can structure it into a Generator Maintenance Agreement, to make it part of the scheduled, and budgeted, yearly maintenance on your standby generator. Load bank testing is not intrusive, and during the test there is no interruption to your facilities power. Most manufacturers agree, a generator set that is frequently run lightly loaded, or never loaded at all, can benefit from being load banked on a yearly basis.
Commercial load bank testing is usually performed as either a two-hour test or a four-hour test.
For residential load bank testing, it would be performed as a one-hour test.
Call today for pricing!